NEETS Module 4  Introduction to Electrical Conductors, Wiring Techniques, and Schematic Reading Pages i  ix, 11 to 110,
111 to 120, 121 to 128,
21 to 210, 211 to 220,
221 to 230, 231 to 240,
241 to 253, 31 to 310,
311 to 320, 321 to 324, 41
to 410, 411 to 418, Index
CHAPTER 1 ELECTRICAL CONDUCTORS LEARNING OBJECTIVES Learning objectives are stated at the beginning of each chapter. These learning objectives serve as a preview of the information you are expected to learn in the chapter. The comprehensive check questions are based on the objectives. By successfully completing the OCCECC, you indicate that you have met the objectives and have learned the information. The learning objectives are listed below. Upon completing this chapter, you should be able to: 1. Recall the definitions of unit size, milfoot, square mil, and circular mil and the mathematical equations and calculations for each. 2. Define specific resistance and recall the three factors used to calculate it in ohms. 3. Describe the proper use of the American Wire Gauge when making wire measurements. 4. Recall the factors required in selecting proper size wire. 5. State the advantages and disadvantages of copper or aluminum as conductors. 6. Define insulation resistance and dielectric strength including how the dielectric strength of an insulator is determined. 7. Identify the safety precautions to be taken when working with insulating materials. 8. Recall the most common insulators used for extremely high voltages. 9. State the type of conductor protection normally used for shipboard wiring. 10. Recall the design and use of coaxial cable. ELECTRICAL CONDUCTORS In the previous modules of this training series, you have learned about various circuit components. These components provide the majority of the operating characteristics of any electrical circuit. They are useless, however, if they are not connected together. Conductors are the means used to tie these components together. Many factors determine the type of electrical conductor used to connect components. Some of these factors are the physical size of the conductor, its composition, and its electrical characteristics. Other factors that can determine the choice of a conductor are the weight, the cost, and the environment where the conductor will be used. CONDUCTOR SIZES To compare the resistance and size of one conductor with that of another, we need to establish a standard or unit size. A convenient unit of measurement of the diameter of a conductor is the mil (0.001, or onethousandth of an inch). A convenient unit of conductor length is the foot. The standard unit of size in most cases is the MILFOOT. A wire will have a unit size if it has a diameter of 1 mil and a length of 1 foot. 11
SQUARE MIL The square mil is a unit of measurement used to determine the crosssectional area of a square or rectangular conductor (views A and B of figure 11). A square mil is defined as the area of a square, the sides of which are each 1 mil. To obtain the crosssectional area of a square conductor, multiply the dimension of any side of the square by itself. For example, assume that you have a square conductor with a side dimension of 3 mils. Multiply 3 mils by itself (3 mils x 3 mils). This gives you a crosssectional area of 9 square mils. Figure 11.  Crosssectional areas of conductors. Q1. State the reason for the establishment of a "unit size" for conductors. Q2. Calculate the diameter in MILS of a conductor that has a diameter of 0.375 inch. Q3. Define a milfoot. To determine the crosssectional area of a rectangular conductor, multiply the length times the width of the end face of the conductor (side is expressed in mils). For example, assume that one side of the rectangular crosssectional area is 6 mils and the other side is 3 mils. Multiply 6 mils x 3 mils, which equals 18 square mils. Here is another example. Assume that a conductor is 3/8 inch thick and 4 inches wide. The 3/8 inch can be expressed in decimal form as 0.375 inch. Since 1 mil equals 0.001 inch, the thickness of the conductor will be 0.001 x 0.375, or 375 mils. Since the width is 4 inches and there are 1,000 mils per inch, the width will be 4 x 1,000, or 4,000 mils. To determine the crosssectional area, multiply the length by the width; or 375 mils x 4,000 mils. The area will be 1,500,000 square mils. Q4. Define a square mil as it relates to a square conductor. CIRCULAR MIL The circular mil is the standard unit of measurement of a round wire crosssectional area (view C of figure 11). This unit of measurement is found in American and English wire tables. The diameter of a round conductor (wire) used to conduct electricity may be only a fraction of an inch. Therefore, it is convenient to express this diameter in mils to avoid using decimals. For example, the diameter of a wire is expressed as 25 mils instead of 0.025 inch. A circular mil is the area of a circle having a diameter of 1 mil, as shown in view B of figure 12. The area in circular mils of a round conductor is obtained by squaring the diameter, measured in mils. Thus, a wire having a diameter of 25 mils has an area of 25^{2}, or 625 circular mils. To determine the number of square mils in the same conductor, apply the conventional formula for determining the area of a circle (A = πr^{2}). In this formula, A (area) is the unknown and is equal to the crosssectional area in square mils, p is the constant 3.14, and r is the radius of the circle, or half the diameter (D). Through substitution, A = 3.14, and (12.5)^{2}; therefore, 3.14 x 156.25 = 490.625 12
square mils. The crosssectional area of the wire has 625 circular mils but only 490.625 square mils. Therefore, a circular mil represents a smaller unit of area than the square mil. Figure 12.  A comparison of circular and square mils. If a wire has a crosssectional diameter of 1 mil, by definition, the circular mil area (CMA) is A = D^{2}, or A = 1^{2}, or A = 1 circular mil. To determine the square mil area of the same wire, apply the formula A = πr^{2}; therefore, A = 3.14 x (.5)^{2} (.5 representing half the diameter). When A = 3.14 x .25, A = .7854 square mil. From this, it can be concluded that 1 circular mil is equal to. 7854 square mil. This becomes important when square (view A of figure 12) and round (view B) conductors are compared as in view C of figure 12. When the square mil area is given, divide the area by 0.7854 to determine the circular mil area, or CMA. When the CMA is given, multiply the area by 0.7854 to determine the square mil area. For example, Problem: A 12gauge wire has a diameter of 80.81 mils. What is (1) its area in circular mils and (2) its area in square mils? Solution (1) A = D^{2} = 80.81^{2} = 6,530 circular mils (2) A = 0.7854 x 6,530 = 5,128.7 square mils Problem: A rectangular conductor is 1.5 inches wide and 0.25 inch thick. What is (1) its area in square mils and (2) in circular mils? What size of round conductor is necessary to carry the same current as the rectangular bar? 13
Solution (1) 1.5 inches = 1.5 inches x 1,000 mils per inch = 1,500 mils 0.25 inch = 0.25 inch x 1,000 mils per inch = 250 mils A = 1,500 x 250 = 375,000 square mils (2) To carry the same current, the crosssectional area of the round conductor must be equal. There are more circular mils than square mils in this area. Therefore: A wire in its usual form is a single slender rod or filament of drawn metal. In large sizes, wire becomes difficult to handle. To increase its flexibility, it is stranded. Strands are usually single wires twisted together in sufficient numbers to make up the necessary crosssectional area of the cable. The total area of stranded wire in circular mils is determined by multiplying the area in circular mils of one strand by the number of strands in the cable. Q5. Define a circular mil. Q6. What is the circular mil area of a 19strand conductor if each strand is 0.004 inch? CIRCULARMILFOOT A circularmilfoot (figure 13) is a unit of volume. It is a unit conductor 1 foot in length and has a crosssectional area of 1 circular mil. Because it is a unit conductor, the circularmilfoot is useful in making comparisons between wires consisting of different metals. For example, a basis of comparison of the RESISTIVITY (to be discussed shortly) of various substances may be made by determining the resistance of a circularmilfoot of each of the substances. Figure 13.  Circularmilfoot. In working with square or rectangular conductors, such as ammeter shunts and bus bars, you may sometimes find it more convenient to use a different unit volume. A bus bar is a heavy copper strap or bar used to connect several circuits together. Bus bars are used when a large current capacity is required. Unit volume may be measured as the centimeter cube. Specific resistance, therefore, becomes the resistance 14
offered by a cubeshaped conductor 1centimeter in length and 1 square centimeter in crosssectional area. The unit of volume to be used is given in tables of specific resistances. SPECIFIC RESISTANCE OR RESISTIVITY Specific resistance, or resistivity, is the resistance in ohms offered by a unit volume (the circularmil foot or the centimeter cube) of a substance to the flow of electric current. Resistivity is the reciprocal of conductivity. A substance that has a high resistivity will have a low conductivity, and vice versa. Thus, the specific resistance of a substance is the resistance of a unit volume of that substance. Many tables of specific resistance are based on the resistance in ohms of a volume of a substance 1 foot in length and 1 circular mil in crosssectional area. The temperature at which the resistance measurement is made is also specified. If you know the kind of metal a conductor is made of, you can obtain the specific resistance of the metal from a table. The specific resistances of some common substances are given in table 11. Table 11.  Specific Resistances of Common Substances The resistance of a conductor of a uniform cross section varies directly as the product of the length and the specific resistance of the conductor, and inversely as the crosssectional area of the conductor. Therefore, you can calculate the resistance of a conductor if you know the length, crosssectional area, and specific resistance of the substance. Expressed as an equation, the "R" (resistance in ohms) of a conductor is 15
Where: ρ = (Greek rho) the specific resistance in ohms per circularmilfoot (refer to table 11) L = length in feet A = the crosssectional area in circular mils Problem: What is the resistance of 1,000 feet of copper wire having a crosssectional area of 10,400 circular mils (No. 10 wire) at a temperature of 20º C? Solution: The specific resistance of copper (table 11) is 10.37 ohms. Substituting the known values in the preceding equation, the resistance, R, is determined as Given: ρ = 10.37 ohms L = 1,000 ft A = 10,400 circular mils Solution: = 1 ohm (approximately) If R, ρ, and A are known, the length (L) can be determined by a simple mathematical transposition. This has many valuable applications. For example, when locating a ground in a telephone line, you will use special test equipment. This equipment operates on the principle that the resistance of a line varies directly with its length. Thus, the distance between the test point and a fault can be computed accurately. Q7. Define specific resistance. Q8. List the three factors used to calculate resistance of a particular conductor in ohms. WIRE SIZES The most common method for measuring wire size in the Navy is by using the American Wire Gauge (AWG). An exception is aircraft wiring, which varies slightly in size and flexibility from AWG standards. For information concerning aircraft wire sizes, refer to the proper publications for specific aircraft. Only AWG wire sizes are used in the following discussion. 16
Wire is manufactured in sizes numbered according to the AWG tables. The various wires (solid or stranded) and the material they are made from (copper, aluminum, and so forth) are published by the National Bureau of Standards. An AWG table for copper wire is shown at table 12. The wire diameters become smaller as the gauge numbers become larger. Numbers are rounded off for convenience but are accurate for practical application. The largest wire size shown in the table is 0000 (read "4 naught"), and the smallest is number 40. Larger and smaller sizes are manufactured, but are not commonly used by the Navy. AWG tables show the diameter in mils, circular mil area, and area in square inches of AWG wire sizes. They also show the resistance (ohms) per thousand feet and per mile of wire sizes at specific temperatures. The last column shows the weight of the wire per thousand feet. An example of the use of table 12 is as follows. 17
Table 12.  Standard Solid Copper (American Wire Gauge) Problem: You are required to run 2,000 feet of AWG 20 solid copper wire for a new piece of equipment. The temperature where the wire is to be run is 25º C (77º F). How much resistance will the wire offer to current flow? 18
Solution: Under the gauge number column, find size AWG 20. Now read across the columns until you reach the "ohms per 1,000 feet for 25º C (77º F)" column. You will find that the wire will offer 10.4 ohms of resistance to current flow. Since we are using 2,000 feet of wire, multiply by 2. 10.4 ohms x 2 = 20.8 ohms An American Standard Wire Gauge (figure 14) is used to measure wires ranging in size from number 0 to number 36. To use this gauge, insert the wire to be measured into the smallest slot that will just accommodate the bare wire. The gauge number on that slot indicates the wire size. The front part of the slot has parallel sides, and this is where the wire measurement is taken. It should not be confused with the larger semicircular opening at the rear of the slot. The rear opening simply permits the free movement of the wire all the way through the slot. Figure 14.  Wire gauge. Q9. Using table 12, determine the resistance of 1,500 feet of AWG 20 wire at 25º C. Q10. When using an American Standard Wire Gauge to determine the size of a wire, where should you place the wire in the gauge to get the correct measurement? STRANDED WIRES AND CABLES A wire is a single slender rod or filament of drawn metal. This definition restricts the term to what would ordinarily be understood as "solid wire." The word "slender" is used because the length of a wire is usually large when compared to its diameter. If a wire is covered with insulation, it is an insulated wire. Although the term "wire" properly refers to the metal, it also includes the insulation. A conductor is a wire suitable for carrying an electric current. A stranded conductor is a conductor composed of a group of wires or of any combination of groups of wires. The wires in a stranded conductor are usually twisted together and not insulated from each other. A cable is either a stranded conductor (singleconductor cable) or a combination of conductors insulated from one another (multipleconductor cable). The term "cable" is a general one and usually applies only to the larger sizes of conductors. A small cable is more often called a stranded wire or cord (such as that used for an iron or a lamp cord). Cables may be bare or insulated. Insulated cables may be sheathed (covered) with lead, or protective armor. Figure 15 shows different types of wire and cable used in the Navy. 19
Figure 15.  Conductors. Conductors are stranded mainly to increase their flexibility. The wire strands in cables are arranged in the following order: The first layer of strands around the center conductor is made up of six conductors. The second layer is made up of 12 additional conductors. The third layer is made up of 18 additional conductors, and so on. Thus, standard cables are composed of 7, 19, and 37 strands, in continuing fixed increments. The overall flexibility can be increased by further stranding of the individual strands. Figure 16 shows a typical cross section of a 37strand cable. It also shows how the total circularmil crosssectional area of a stranded cable is determined. Figure 16.  Stranded conductor. 110
NEETS Table of Contents
 Introduction to Matter, Energy,
and Direct Current
 Introduction to Alternating Current and Transformers
 Introduction to Circuit Protection,
Control, and Measurement
 Introduction to Electrical Conductors, Wiring
Techniques, and Schematic Reading
 Introduction to Generators and Motors
 Introduction to Electronic Emission, Tubes,
and Power Supplies
 Introduction to SolidState Devices and
Power Supplies
 Introduction to Amplifiers
 Introduction to WaveGeneration and WaveShaping
Circuits
 Introduction to Wave Propagation, Transmission
Lines, and Antennas
 Microwave Principles
 Modulation Principles
 Introduction to Number Systems and Logic Circuits
 Introduction to Microelectronics
 Principles of Synchros, Servos, and Gyros
 Introduction to Test Equipment
 RadioFrequency Communications Principles
 Radar Principles
 The Technician's Handbook, Master Glossary
 Test Methods and Practices
 Introduction to Digital Computers
 Magnetic Recording
 Introduction to Fiber Optics
